These clearances MUST be continuous from the street to the final spa location unless using a Crane. For more information, please visit our Prep Location page.
The Hot Tub must have a solid, level foundation.
- 4inch thick Concrete (recommended)
- Handi Pad (can be purchased here)
Hot tub must be level for consistent water level and proper filtration.
240V / 50A
||8 Gauge (black/red)
||8 Gauge (white)
||10 Gauge (green)
All circuits MUST be GFI Protected at the main electrical panel or at a remote disconnect.
Must include SealTite whip at spa end with wires extending at least 6″ past end of SealTite. Length of SealTite whip must be long enough to reach the Control Pack (See Spa Diagram for the location of the Control Pack)
For more information on spa electrical requirements, please visit our Spa Electric page.